3TK2907 Datasheet PDF learn more.
Part number : 3TK2907
Functions : This is a kind of semiconductor. Contactor Safety Combination.
Pin arrangement :
Package information :
Manufacturer : Siemens
The texts in the PDF file :
Contactor Safety Combination Instructions 3TK2803, 3TK2804 3TK2907, 3TK29.3 DIN EN 60439 Part 1/ VDE 0660 Part 500 (04.94) Order No.: 3ZX1012-0TK20-1AA2 English WARNING: HAZARDOUS VOLTAGE CAN CAUSE ELECTRICAL SHOCK AND BURNS. .cDoImSCONNECT POWER BEFORE PROCEEDING WITH ANY WORK ON THIS EQUIPMENT. Operation permissible in switchgear cabinet with degree of protection IP 54 only! Application The contactor safety combinations can be used in EMERGENCY-OFF circuits and for monitoring protective devices (e.g. protective screens). Functions and connections The internal control circuit of the contactor safety combination is designed according to DIN EN 60204, Part 1 (VDE 0113, Part 1), para. 126.96.36.199, so that in the case of a fault in one of the contactor relays the function of the safety circuit is maintained. The supply voltage must meet the requirements of the DIN EN 60204 (VDE 0113, Part 1) (the terminals “L-/N; A2“ must be connected to that side of the control current circuit which is linked to the protective conductor system).The contacts of the contactor relays are checked for proper opening and closing in every ON and OFF cycle of the machine to be switched. This is, for instance, done by – connecting and disconnecting the control voltage with the main switch, – activating and deactivating the EMERGENCY-OFF unit – opening and closing of the protective screen. For circuit diagrams, see: Fig. III: EMERGENCY-OFF circuit Fig. IV: Protective screen monitoring (A=door open; B=door closed) Fig. V: EMERGENCY-OFF with expansion module (no delay) Fig. VI: EMERGENCY-OFF with time-delay module For internal circuit diagrams, see Low-Voltage Control Equipment, Switchgear and Systems Catalog. Note: The units are tested by the BIA. The external control circuit connections are shown for example only; the actual connections must be defined by the user on the basis of a risk assessment. Further applications available upon request. Installation For dimension drawi [ … ]
3TK2907 PDF File